Saturday, January 9, 2010
After 2 minutes the furnace would act up. The flame sensor was cleaned and the problem persisted. Notice the tube moving in the video to the pressure switch. It was determined that the draft motor was not keeping up pressure on the switch. The draft blower was removed , the blower wheel was cleaned and the furnace was fixed.